Pipeline Sizing
#1
Posted 10 February 2010  02:53 AM
I am trying to figure out how a 6" size has been selected for a gas injection pipeline (above Ground) with a max operating flow rate 15.5 to 56.5 mmscfd.
Design data is as below.
Nominal size = 6"
Design Pressure = 280 barg
Design Temp. = 134
Fluid Catagory(ISO 13623) = E
Density = 183  257 Kg/m^3
Viscocity = 0.013  0.014 cp
Dew point = 71.91
The velocity is much higer than the recommended standards that I have access. I do'nt have the basic engineering documents for this completed project.
Would be of much help if anyone could guide me to find the criteria applied for above sizing.
Regards,
U.Narayanan
#2
Posted 10 February 2010  07:34 AM
If I assume compressibility factor is 1, that 6 in pipe seem normal which have the velocity around 5 m/s.
And momentum (roV^{2}) around 7000 kg/ms_{2} which have the criteria is 20000 kg/ms^{2} for very high pressure.
#3
Posted 10 February 2010  12:33 PM
There is a missing data, which is compressibility factor.
If I assume compressibility factor is 1, that 6 in pipe seem normal which have the velocity around 5 m/s.
And momentum (roV^{2}) around 7000 kg/ms_{2} which have the criteria is 20000 kg/ms^{2} for very high pressure.
Thanks for the guidance. The flow rate need to be corrected to the operating conditions, if I understood it correctly.
Regards,
Narayanan
#4
Posted 10 February 2010  03:52 PM
Hi all,
I am trying to figure out how a 6" size has been selected for a gas injection pipeline (above Ground) with a max operating flow rate 15.5 to 56.5 mmscfd.
Design data is as below.
Nominal size = 6"
Design Pressure = 280 barg
Design Temp. = 134
Fluid Catagory(ISO 13623) = E
Density = 183  257 Kg/m^3
Viscocity = 0.013  0.014 cp
Dew point = 71.91
The velocity is much higer than the recommended standards that I have access. I do'nt have the basic engineering documents for this completed project.
Would be of much help if anyone could guide me to find the criteria applied for above sizing.
Regards,
U.Narayanan
U Narayanan,
A lot of inputs are missing for any evaluation to be done:
1. What is the composition or molecular weight of the gas?
2. You mention design pressure as 280 barg. What is the operating pressure of the pipeline?
3. What pressure drop are you alllowing from source to destination (starting point to termiantion point)?
4. What is the length of the pipeline?
Other points to take care of:
1. Compressibility factor (Z) at high pressures would never be 1. It would be always less than 1 and you need to calculate the 'Z' value at your operating pressure & temperature using an 'Equation of State' such as RK (RedlichKwong), SoaveRedlichKwong (SRK), PengRobinson (PR).
2. Once you have the 'Z' factor, you can calculate the density of the gas at the given operating temperature & pressure by the equation
rho = P*M / R*T*Z
where:
rho = density @operating Pr/Temp, kg/m^{3}
P = operating pressure, bar (abs)
R = universal gas constant, 0.08314
T = operating temperature, K
Z = compressibility factor, dimensionless
3. You cannot calculate the gas velocity based on the volume flow given in standard conditions (SCFD). Your velocity has to be calculated based on the volume flow at the operating pressure & temperature.
4. First you need to convert your volume flow in standard conditions to mass flow by multiplying with the gas density at standard conditions. Gas density at standard conditions (1.013 bara & 15 deg C) is calculated by dividing the molecular weight of the gas by 23.7 (MW/23.7).
5. Once you have the mass flow rate & the gas density calculated as per step 2, actual volume flow can be calculated as "Mass/Density'.
6. Once you have calculated the actual volume flow as per step 5 with the units as m^{3}/h, then the velocity in the pipeline can be calculated as below:
v = 3.5368E4 * Q / d^{2}
where:
v = velocity, m/s
Q = volume flow rate, m^{3}/h
d = Internal diameter of the pipe, m
7. For long pipelines carrying gas you can allow normal operating velocities of 3035 m/s without any problems. Some earlier guidelines used to restrict the gas velocities to a maximum of 18 m/s (60 ft/s).
8. Where pressure drop is critical, the velocities would be restricted by the pressure drop criteria. You may refer section 6.4 of 'Norsok' Std. P001 which has a table giving the recommended maximum pressure drop per 100 m for the operating pressure range of the gas. The standard is available as a free download.
Hope this helps.
Regards,
Ankur.
#5
Posted 10 February 2010  11:24 PM
FYI
Max operating pressure is 260 barg.
Fluid type (Liquid, Gas, Polyphasic) : Gas ( as given in the document I have).
The error was that I calculated the velocity using flow rate at standard conditions. I did right by asking above question to the experienced friends in this forum .
Thanks again and regards,
U.Narayanan
#6
Posted 11 February 2010  09:36 PM
Forget also the Z and other parameters, what you need is the criteria and nothing else. The detailed calculations in a suitable software must be carried out by yourself.
Check also possible hydrate formation. The maximum velocity suggested for high pressure (above 80 barg) pipelines is about 10 m/s allowing a rhov2 of about 15000 Pa.
Important: allowable delta P vs. delivery pressure
Best Regards,
GERARDO VILLAMIZAR P.
#7
Posted 12 February 2010  02:57 AM
Please forget all these contributions,
Forget also the Z and other parameters, what you need is the criteria and nothing else. The detailed calculations in a suitable software must be carried out by yourself.
Check also possible hydrate formation. The maximum velocity suggested for high pressure (above 80 barg) pipelines is about 10 m/s allowing a rhov2 of about 15000 Pa.
Important: allowable delta P vs. delivery pressure
Best Regards,
GERARDO VILLAMIZAR P.
Gerardo,
Two questions:
1. What if you don't have a suitable software as you call it? Does it mean that you cannot calculate the velocity by hand calculations? I am certainly not dependent on 'suitable software' as you call it & I suggest any young engineer not to depend on socalled 'suitable softwares'. Calculating velocity by using 'suitable software' would be an insult to my engineering skills.
2. What is the source of your information for maximum velocity of 10 m/s (above 80 barg)? You are not giving refernce to any source. Per Norsok std. P001, for singlephase gas lines with continuous flow where pressure drop is not critical the maximum allowable velocity can be calculated as follows:
v = 175 * (1/rho)^{0.43}
or 60 m/s whichever is less
where: rho = density of gas in kg/m3
In practice, the above velocity values are a little too high for my comfort but I have seen singlephase gas lines operate at 100115 ft/s (3035 m/s) without any problems provided that they are well designed (proper routing, well supported & without any solid particle contamination).
Regards,
Ankur.
Similar Topics
Software For Separator SizingStarted by Guest_Propacket_* , 29 Oct 2014 



Psv Outlet Pipe Sizing To AtmStarted by Guest_abir_* , 20 Oct 2014 



Blow Down Valve SizingStarted by Guest_rkvizag04_* , 06 Oct 2009 



Fire Sizing  Latent Heat Of VaporizationStarted by Guest_MelB_* , 30 Jul 2014 



What Is Cluster And Pipeline Project ( Epc)?Started by Guest_ashb_* , 18 Oct 2014 

